OISD 144 VOLUME 1 DESIGN CRITERIA Integration of Natural
|Title||:||OISD 144 VOLUME 1 DESIGN CRITERIA Integration of Natural|
|Date Added||:||25 January 2012|
Summaryoisd 144 fire protection facilities design criteria all lpg storage vessels ... capacity of main fire water pump min 2 storage tanks are provided if steel tanks ...
... INTRINSICALLY SAFE OISD 144 FIRE PROTECTION FACILITIES The Gas Monitoring system - early warning for gas concentration below the LEL (lower explosive limit).
Rule 169 Rule 42 is on Duty of medical officer onboard ( Ensuring adequate hygiene ... OISD OISD ONGC OISD OISD ONGC OISD OISD ONGC ...
... namely OISD 144, OISD 150, OISD 169 as amended time to time and such other standards as may be applicable and same should be approved by PESO and other ...
be equipped with Fire Fighting Facilities as required as per OISD 169 or OISD 144 standards. 8.
... Evaluate Element Criteria Enforce Practicality Criteria Update FE Bulkdata Generate VIEW Results Converged ? no yes Input File Detail Analysis Tool Output File FE Result ...